Cambopura Glass Factory - Cambodia
Phnom Penh, Cambodia
Cambopura Glass Factory has contacted GK Engineering to support them because at first for a troubleshooting on their main breaker and to conduct on a second phase an audit on standard compliance with their electrical installation
We did record their power during half day with a power harmonic analyser to identify possible issues.
We proved that the Main breaker was sensitive to Harmonics and therefore tripped because of harmonics.
We have verified with computerised calculation the entire installation and have produced a full report on what was to be corrected, oversized, overspecified or unsafe.